Note: All Power Supply and Test Ckt. Connections Are Not Shown For Clarity. See Fig. 2
For Complete Individual Relay Wiring
TRIP COIL REQUIREMENTS
A circuit breaker or switch used with the Type GC Ground Fault System must have a trip coil capable of operating reliably
at 55% of rated voltage. Inrush current must not exceed 50 amperes at rated voltage. Sealed current must not exceed 10
amperes unless coil clearing contacts (52a) are used. Coil clearing contacts are required for trip coils not rated for
continuous duty at 120 Vac.