Burner control panel-adjust materiel temperature, if
temperature is out of tolerance by more than 50, by
adjusting the set point on the Stack Control by the
number of degrees that the materiel is in error.
Burner control panel-verify that the Damper Control is
Control is maintaining a static pressure at the burner face
of approximately negative .25 to negative .50 inches.
If static pressure is out of tolerance select MANUAL by depressing Damper Manual/Auto switch
(light will illuminate-to show manual position). (Panel D)
Burner control panel-to obtain a negative -.50 in.
pressure of greater value open damper by PRESSING
the Damper Open button to arrive at proper static
pressure. Opening the exhaust damper will decrease
back pressure. After the proper pressure is obtained
return Damper switch to AUTO.
< 6.0 in
Corner panel-Baghouse Differential Pressure monitor
this in conjunction with the Damper Control. Baghouse
differential pressure should not exceed approximately 6.0
in. If it is above this value, bag efficiency has decreased
and needs to improve. Lower production rate to allow
Differential pressure may decrease after a period of time.
Motor control panel-monitor the frequency meters on a
regular basis. They should read 60 hertz + or-1 (not
required when on utility power).
Motor control panel-surge bin loading. Alarm will sound
and red light on Surge Bin High Level will flash when bin
is nearing capacity.