The flame amplifier module is installed in the second
set of guide channels found in the EB700 FLAME-
Do not force the module into position.
CAUTION: Remove power from the wiring base
before trying to replace the Flame Amplifier Module.
Terminal Wiring Base
When wiring to the FLAME-MONITOR wiring base,
scanner terminal S2 must be grounded when using
flame rod on photocell scanner. When using an infrared
scanner (48PT2), ground S2 on all EB700s labeled
"ENG CODE 00". All other ENG CODE models do not
require that S2 be grounded. Do not ground S2 when
using ultra violet scanners.
page 3 - 1155