If the process system, such as a rotary dryer application, has a fabric filter dust collector (baghouse),
consult the manufacturer for recommended baghouse temperature limitations.
See Section G, Example 3 for entering the desired Alarm Setpoint.
B. RECEIVING AND INSPECTION
Upon receipt, check each item on the bill of lading and/or invoice to determine that all equipment has been received. A
careful examination should be made to ascertain If there has been any damage in shipment.
For optimum use of the Hauck panel, it Is suggested that the Hauck drawings provided be referred to for
recommended switch and valve installation and wiring. In the event any recommended switch application
is not utilized, It will be necessary to connect a jumper wire(s) between appropriate terminals on the
control panel or burner junction box, as applicable Such determination remains the responsibility of the
customer, based upon his application, accepted safe installation and operating procedures, and any
applicable governmental regulations.
Locate the panel on a firm support in an area which is protected from the weather and free of vibration.
The operating specification of 32-142 deg F., 595% relative humidity, noncondensing, should be
considered in selecting the location for the panel.
Provide 120 Vac single phase GROUNDED NEUTRAL power to the burner control panel. It is recommended that the
customer provide and install a master disconnect switch to interrupt power service to the panel. Maintain polarity as
Indicated on the drawings provided when wiring the main power source to the panel.
Install a Heavy gauge (No. 12 AWG minimum) ground wire between the panel ground terminal and "Earth" ground.
Install and wire the burner and system limit switches, fuel valves, flame scanners, ignition transformer, and other
associated components as shown in the drawing provided. SEE THE CAUTION above pertaining to certain aggregate
Install the Hauck stack temperature thermocouple, as applicable, in the dryer exhaust duct to sense exhaust gas
temperatures. Install the thermocouple as detailed In figure 1.