HEATER INSTALLATON CHECKLIST
Remove all shipping labels, bands and tape from the sight glass, panel box, gauges, thermometers,
valves, etc. and inspect for shipping damage.
Open the supply valve, the return valve, the by-pass valve and the suction line valve.
Connect the Heat Transfer Fluid supply and return lines.
Check the power supply for correct voltage. Connect the power supply.
Grease the circulating pump with high temperature grease.
Fill the system with heat transfer fluid. Refer to Section 3.3 for details.
Fill circulating pump bearing lubrication cavity with heat transfer oil. Refer to Section 6.11.
Connect the fuel supply line(s).
Check the rotation of the circulating pump motor and the burner blower motor. If both are rotating in the
wrong direction, reverse any two of the incoming power leads at the main circuit breaker.
Start the burner. SECTION 5: BURNER OPERATION outlines the start-up procedure for the various