12. [MAN/AUTO] KEY: Alternately selects Manual or Automatic control mode.
13. [AUTO TUNE] KEY: Starts the Automatic Tuning procedure. KEY ERROR appears If Auto Tune disabled.
14. [RUN/HOLD] KEY: Not used.
15. [?] KEY: Used to increase Set Point, % Output or Configuration values.
16. [ ] KEY: Used to decrease Set Point, % Output or Configuration values.
CHANGING THE SET POINT
Press the [LOWR DISP] key until SP and the current set point appears in the lower display
Press and hold the [?] key to increase the set point value. To make changes more quickly, press the [ ] key while
holding [ ] key. This will shift the changing digit one place to the left. To decrease the set point value, reverse the
POSITIONING THE CONTROL MOTOR IN THE MANUAL MODE
Press the [AUTO/MAN] key to place the Controller in the Manual Mode. The MAN indicator will come ON and the
lower display will automatically change to show % OUT.
Press and hold the [?] key to increase the % Output value To make changes more quickly press the [ ] key while
holding [?] key This will shift the changing digit one place to the left.
To decrease the % Output value, reverse the above procedure.
CHANGING THE ALARM SET POINT
Press and hold the [SET UP] key until the display reads SETUP ALARMS.
Press the [FUNC] key once to change the lower display to A1S1 VAL. The upper display will show the current
alarm set point. Use the [?] or [ ] arrow key to change to the desired set point
Press the [LOWR DISP] key to exit the Set Up mode and return the controller to normal operation.
If the process system, such as a rotary dryer application, has a fabric filter dust collector (baghouse),
consult the manufacturer for recommended baghouse temperature limitations.
H. CONFIGURATION RECORD SHEET
Hauck part number 48736; Honeywell model DC3004-0-OOA-1-00.
Cold junction jumper in position W1. Alarm relay jumper In position W7 See page 3-21 of instruction manual for jumper