M-26 Check for proper operation of operator mechanism
Test for ON" "OFF" RESET" action plus door inter
lock If necessary, FA and KA circuit breaker
operators can be adjusted, refer to Section 1 20
page ] 3.
M-27 Check all fuses and use clips Replace any parts
that show signs of overheating or arcing.
M-28 Check starter contacts Replace any that are badly
worn or pitted
M-29 Check for proper operation of starters, relays,
and other control devices